ANNUAL ELECTRICITY BILL BY £37,500 PER ANNUM
Part of this process involved surveying the facility, with a view to identifying actions to reduce energy consumption. It became clear that voltage optimisation would be beneficial in reducing the Manchester facility’s energy consumption and offer considerable cost savings too.
Data logging allowed us to measure consumption and provide baseline figures. During this process it became clear that the site suffered from large loading swings which made it unsuitable for standard forms of fixed voltage optimisation. Voltage optimisers were used to optimise the voltage to a single piece of equipment, localised area or an entire building. They can be supplied with fixed or variable outputs, with or without power factor correction. In this instance a voltage tracking (stabilised) optimiser was designed to deal with the specific issues identified, and to achieve the maximum possible energy saving. The unit was installed and further data logging carried out to measure the savings.
Reduction in Consumption PA – 463,176 KWh
Reduction in Electricity Cost PA –£40,226.84
Reduction in CO2 Emissions PA –243 Tonnes
Total Project Cost – £71,061.52
Payback Period-21.2 Months